Medium Voltage TerminationDelivery term:The date of payment from buyers deliver within days
- Total supply:
The date of payment from buyers deliver within days
Browse the number:
Heat Shrink Termination For MV Cables Up To 42kV
Design of Termination
Provides a universal system for indoor and outdoor medium voltageterminations for paper or polymeric insulated cables.
1. Electrical Stress Control
Yellow stress relief mastic is laid around the end of the screen cut.Stress control tube, together with stress mastic, is used tosmooth out the electrical field at the cable end.
2. Excellent Anti-tracking Properties
Anti-tracking insulation tubes and rain sheds have an excellenttracking and erosion resistance. This ensures terminationsdo not track even in severe service conditions.
3. Additional Creepage
Anti-tracking rain sheds increase surface creepage distance.
4. Moisture Sealing
Durable sealing is achieved by hot-melted adhesive on the insideof sealing tube and anti-tracking insulation tube. In case of 3-corecables, the crutch area is sealed and protected with an adhesivecoatedbreakout which is installed over the cores and the end of oversheath.
5. Earth Connection
Either soldering or solderless earth connection is available toconnect metal screen or armour to ground. For cables with wirescreen, copper wires are imbedded in the sealing mastic to preventany corrosion by moisture sealing.
1.Lugs need to be ordered separately.
2.RSWY-3 is for cables with copper wire screen without armour.
3.3.Solderless earth connection have to be ordered separately as follows:
For cables with copper wire screen and wire armour, add suffix –WA. For example, 6kVRSWY-3/1-WA.
For cables with copper tape screen with armour wire,add suffix –X. For example, 6kVRSWY-3/1-X.